A transmission line having a length of less than 80 km is considered a short transmission line. The operating voltage of this line is in terms of 20kV.
Due to the small length and low operating voltage, the capacitance in a short transmission line is negligible. But in case of Long transmission line and Medium transmission line, we need to consider capacitance.
There is the only effect of resistance and inductance considered while modeling a short transmission line. The equivalent circuit or graphical representation of a short line is as shown below figure.
When current flows through the circuit, a voltage drop occurs due to resistance and inductance. Due to resistance, IR drops occurs. And due to inductive reactance, IXL drop occurs.
Therefore, some amount of voltage drops in the circuit and the value of receiving end voltage is less than the sending end voltage.
The phasor diagram of this system is as shown in the below figure.
From the above Phasor diagram;
Sending End Power Factor;
Receiving End Power =VR IR cosфR
Losses in Line = I2R
Sending end power = Power at Receiving end + Line losses
ABCD Parameter for Short Transmission Line
From the above figure, we can say the sending end current is the same as the receiving end current. And sending end voltage is a summation of receiving end voltage and the drop across the line.
Now, compare these equations with the equations of ABCD parameters;
If we compare above equations, we can conclude that;
324 total views, 1 views today